Ajna Bollard 
ID : 24758
Input power : 24W LED
Technical Description
K-Lite Bollard luminaire designed for surface mounted. Symmetrical light distribution. Luminaire made of extruded aluminium alloy (grade 6063), die-cast aluminium components of high corrosion resistance and non corrosive stainless steel fasteners. Reflector system made of spun aluminium (powder coated white). Clear polycarbonate diffuser. Mounting plate 202mm diameter x 8mm thick with 4 elongated holes 15 x 20 to suit M12 bolts at PCD 140 for surface mounting on floor. Single cable entrance via PG7 cable gland. Protection class IP65. Mechanical resistance IK08. Pure polyester powder coated RAL 9004 Black, RAL 9007 Grey aluminium, RAL 7016 Anthracite grey & Graphite grey. Available colour temperature 2700K / 3000K / 4000K / 5700K. Colour rendering index (CRI)>80. K-Lite LED module with expected service life of at least 60,000 operating hours. Prewired with LED driver and suitable for operating on 240V, 50Hz single phase ac supply. Driver efficiency >88%, Power factor >0.95, THD <10%, Surge protection 4KV. Luminaire dimension : 200mm diameter x 906mm height. CE & BIS Certified. Inhouse NABL accredited lab.