Nimbus Bollard
ID : 24727
Input power : 16W LED
Technical Description
K-Lite Bollard luminaire designed for surface mounted. Symmetrical light distribution. Luminaire made of square extruded aluminium tube (grade 6063) with pressure die cast aluminium components of high corrosion resistance and non corrosive stainless steel fasteners. Clear polycarbonate diffuser. Pressure die cast aluminium mounting plate 121 square x 4mm thick with 3 elongated holes 15 x 10 to suit M8 bolts at PCD 70 with pure polyester powder coating.The base plate have a cable entry hole of 30mm dia at the center. This mounting plate along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foundation. Protection class IP65. Mechanical resistance IK08. Pure polyester powder coated RAL 9004 Black, RAL9007 Grey aluminium, RAL 7016 Anthracite grey, Graphite grey. Available colour temperature 2700K / 3000K / 4000K / 5700K. Colour rendering index (CRI)>80. K-Lite LED module with expected service life of at least 60,000 operating hours. Prewired with LED driver and suitable for operating on 240V, 50Hz single phase ac supply. Driver efficiency >80%, Power factor >0.9, THD <10%, Surge protection 2.5KV. Luminaire dimension : 121mm square x 500mm height. CE & BIS Certified. Inhouse NABL accredited lab.