Dice Bollard
ID : 24596
Input power : 1 x 6W / 2 x 6W LED
Technical Description
K-Lite Bollard luminaire designed for surface mounted. Symmetrical light distribution. Luminaire made of rectangular extruded aluminium tube (Grade 6063), aluminium components and non corrosive stainless steel fasteners. Clear toughened glass. Pressure die cast aluminium mounting base 173mm x 104mm with 3 Nos. of Ø9 holes. This mounting base along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foundation. Protection class IP65. Mechanical resistance IK07. Pure polyester powder coated RAL 9004 Black / RAL 9007 Grey aluminium / RAL 7016 Anthracite grey / Graphite grey. Available colour temperature 2700K / 3000K / 4000K / 6500K. Colour rendering index (CRI)90. K-Lite LED module with expected service life of at least 60,000 operating hours. Prewired with LED driver and suitable for operating on 240V, 50Hz single phase ac supply. Driver efficiency >80%, Power factor >0.9, THD <10%, Surge protection 3KV. Luminaire dimension : 166mm / 225mm length x 173mm width x 900mm height. CE & BIS Certified. Inhouse NABL accredited lab.